An incinerator represents a complete solution to the problem of disposal of all hospital waste types. The liquid fuel is diesel. The incinerator should meet the environment standards.
Expected Technical specifications
The incinerator shall be fully self contained.
The incinerator plant shall incorporate a control panel for its operation. On the control panel we shall have a visual display of the chamber temperatures. This visual display must control and monitor the incinerator and his performance.
Capacity of destruction in weight shall be 60 Kg/h.
It should be able to operate not less than 10 hours/day
This incinerator must be able to destruct all combustible wastes produced by hospitals, private clinics, laboratories, institutes, etc…
Design Specification : Types A, B, C, D, and E of medical waste
“PYROLYTIC” combustion, by controlling the gasification of waste.
The incinerator must avoid the release of black smoke and fine dust, during the loadings.
It shall be able to reduce the volume of wastes by 98%.
It shall be able to hold emission in the second burn with gas residence of not less than 2 seconds.
The incineration should be completely free from visible smoke as well as offensive odours.
1.0The primary ignition burner shall providing ignition of the waste to 850 °C and must switch off to conserve fuel.
The primary combustion chamber shall be constructed from heavy steel plate and the unit is internally lined with a complete layer of hote face refractory and high efficiency insulation.
The Internal diameter of the Chimney at least: Ø 400 and its height: 8 m
The Volume of the combustion chamber at least: 1.200 L
The Dimension of the door for loading in cm at least: 70×70.
Burner operation should be Automatic On/Off
Fuel : diesel
Manufacturer to provide necessary information for the best of the installation